Gestra markalı, ürün kodu TRV5-40 olan Gestra TRV5-40 ürününün fiyat ve detaylarını aşağıda inceleyebilirsiniz. Teklif almak için online teklif formunu doldurunuz.
Detaylı Bilgi - Gestra TRV5-40 temperature transmitter TRV 5-40
The temperature transmitter TRV 5-40 is designed for the connection of three temperature sensors TRG 5-6x (platinum resistance thermometer Pt 100 to EN 60751). The temperatures measured by the temperature sensors are converted by the temperature transmitter TRV 5-40 and sent to the CAN bus in the form of a data telegram. The data are transferred via CAN bus, using the CANopen protocol. The temperature transmitter TRV 5-40 can be used as: ? safety temperature monitor / limiter in conjunction with a temperature sensor type TRG 5-6x and the control unit NRS 1-40.1 / NRS 1-40.2 and ? temperature monitor & limiter in conjunction with one or two temperature sensors TRG 5-6x and the control unit TRS 5-40 or any other equipment that is approved for this application. The equipment combination can be used for monitoring, limiting or control purposes in steam plants and (pressurised) hot water installations according to TRD and EN 12952 and EN 12953.
The temperature transmitter TRV 5-40 consists of the safety part for temperature limiting and the part for temperature monitoring & control. The safety part is connected with the temperature sensor. The temperature sensor detects the temperature and sends the measured values to the safety part of the temperature transmitter, where the measured values are recorded redundantly and monitored. The adjustable temperature limit TMAX (°C), the actual temperature and system malfunctions are indicated by the temperature transmitter. The temperature sensing element on the electronic insert monitors continuously the temperature inside the transmitter housing. An automatic self-testing routine checks every 10 seconds the safety and reliability of the functions of the temperature sensor and the detection of the measured values. The actual temperatures, the exceeding of the adjusted temperature limit TMAX (°C), the result of the periodic self test and the temperature inside the transmitter housing are sent as a data telegram via CAN bus to the control equipment NRS 1-40.1 / NRS 1-40.2. Regardless of the safety part two additional temperature sensors TRG 5-6x can be used for temperature monitoring & control in order to measure further actual temperature values. These readings are also sent as data telegrams via CAN bus and will be evaluated e. g. by the control unit TRS 5-40.